- Sales Manager: Manager Zhu
- Sales Hotline: 13718739688 (Beijing)
- Phone: 18351045119 (Yangzhou)
- Fax: 18351045119
- Email: firstname.lastname@example.org
- Address of Company: Putou Industrial Zone, Jiangdu, Yangzhou City, Jiangsu Province
- Bao'an Fire Box Factory talk about fire equipment installation ...
- Baoan Fire Fighting teaches you how to identify fire box ...
- How to use fire boxes more safely
- Fire box manufacturers analyze the maintenance methods of fire box ...
- How to buy fire equipment?
- Summer hot weather is approaching ...
- Use experimental methods to tell you why ...
- Baoan fire box manufacturers teach you how to check and eliminate ...
Fire box manufacturers popularize the main points about the installation and use of fire equipment
- Author: xiaofangyuan
- Release time: 2018-11-25 19:11:56
- News browsing popularity: Times
Yangzhou Baoan Fire Fighting Equipment Co., Ltd. produces "Qionghua" brand series of products: fire box , stainless steel fire box , fire hydrant box , rolling fire box , water film fire box , lined fire hose series products, indoor fire hydrant Pressure-reducing and pressure-stabilizing series, fire water gun, interface series products, fire emergency light series and fire alarm button, fire hose series products, etc.
You are welcome to inquire and order the products you need. 24-hour service phone: 18351045119 13718739688.
1. The fire box manufacturer sets a bus short-circuit isolator on the bus of the fire-fighting system. One isolator with a maximum of 32 points is set according to the fire protection zone. 2. Except for the controllers installed in the fire control room of each building over 100m, each fire detector, hand alarm and module should not cross the refuge floor. 3. A fire control room should be set up in a building with fire linkage function. 4. The fire control room shall have corresponding as-built drawings, descriptions of the control logic relationships of each sub-system, instructions for use, system operating procedures, emergency plans, duty systems, maintenance systems and cardboard records. 5. It is strictly forbidden to pass through fire control facilities without electrical lines and pipelines unrelated to fire protection facilities. 6. It is allowed to use the fire control room with the weak current system, but there should be a clear interval. 7. The fire automatic alarm system should be equipped with fire sound and light alarms, and all fire sound and light alarms in the building should be activated after confirming the fire. 8. When the fire sound alarm is set with voice prompt function, a voice synchronizer should be set at the same time.